- Rack side panel
The Net-Access S-Type Cabinets shall consist of a welded and assembled steel frame construction available in 600mm (23.6in.), 700mm (27.6in.), and 800mm (31.5in.) widths, 1068mm (42.0in.), and 1220mm (48.0in.) depths, and 42 RU, 45 RU, and 48 RU heights. The top of cabinet includes molded edge protection and snap-in covers, and pre-installed in cable entry openings to prevent air leakage. Cabinets shall include front single hinge doors with 69% open perforation and rear perforated or solid split doors. Cabinets shall have rails with provisions for rear cable management fingers (some finger sold separately) or to accept Zero RU QuickNet Style Inserts. Cabinet shall have one set of PDU brackets. The entire cabinet shall be fully electrically bonded, including equipment rails, door, and side panels. Single point bonding locations shall be available at the top and bottom of each cabinet. Cabinets shall have a 1360kg (3000 lbs.) load rating and 1136kg (2500 lbs.) rolling load rating.